Note: You are seeing this text-only version of our site
because you are using an older browser that is not standards-compliant.
How to upgrade to a FREE standards-compliant browser.
Some Netscape 7 and Mozilla users may see this warning in error.
to fix the problem.
Back to Company
Profiplug converts transmitted data from devices in MODBUS RTU standard into data in Profibus DP standard, enabling the access of measurement results into Profibus DP network.
Communication Profibus Side: Interface: 9-pin D-sub connector (female) ; Tranfer: Method RS-485 Half-duplex ; Transfer Cable: Shielded twisted pair; Electrical Insulation: Optoinsulated; Communication mode: Profibus DP; Address: 1 to 126; baud Rate: 9.6 kBaud to 93.75 kBaud
Communication Modbus Side: RS-232 Interface: Vertical connecting terminal pitch 5,08 mm; Tranfer Method: RS-232, Half-duplex; Transfer Cable 3: wire (Tx, Rx and signal ground); Electrical Insulation: n.a.; RS485 Interface: Vertical connecting terminal pitch 5,08 mm; Tranfer Method: RS-485, Half-duplex; Transfer Cable: 3 wire (A, B and signal ground); Electrical Insulation: n.a.; Communication mode: Modbus RTU; Address: 1 to 247; baud Rate: 9.6 kBaud to 38.4 KBaud.
See attached spec. sheet.
Copyright © 2005-2017 Modbus Organization, Inc.
PO Box 628 Hopkinton, MA 01748. All rights reserved.
By using Modbus.org, you accept the terms of our visitor