Note: You are seeing this text-only version of our site
because you are using an older browser that is not standards-compliant.
How to upgrade to a FREE standards-compliant browser.
Some Netscape 7 and Mozilla users may see this warning in error.
to fix the problem.
Back to Company
Accepts and "reads" the HART Digital Protocol Signal that rides on the 4-20mA wires of a Smart HART multivariable transmitter or valve; Converts the HART digital signal to serial (RS-485) Modbus RTU communication protocol to allow smart transmitters and valves to interface with Modbus-based systems.
Provides additional analog signals proportional to a multivariable transmitter's primary, second, third or fourth variables, or to user-selectable valve parameters such as stem position; High/Low process and loop diagnostic alarms; Sets up as a Primary or Secondary Master, or in "Listen" Mode; Normal or Burst HART Modes; Large, 5-digit display; Isolated output channels
4-Wire, Line-Powered (24Vdc); High-density and RFI-resistant aluminum DIN-style (G-type and Top Hat rails)
Copyright © 2005-2018 Modbus Organization, Inc.
PO Box 628 Hopkinton, MA 01748. All rights reserved.
By using Modbus.org, you accept the terms of our visitor