Note: You are seeing this text-only version of our site
because you are using an older browser that is not standards-compliant.
How to upgrade to a FREE standards-compliant browser.
Some Netscape 7 and Mozilla users may see this warning in error.
to fix the problem.
Back to Company
Remote Terminal Unit
Remote Terminal Unit designed for electric power utility and telecommunications industries
Output relays can handle 0.6 Amps at 125Vac or 2 Amps at 30Vdc and can be used in Select-Before-Operate or Direct Operate modes; Eight status inputs can be independently configured for Active-HI and/or Active-LO operation; Two RS-232 ports and one Ethernet port; Can be configured for DNP 3.0, Modbus, PG&E, Landis & Gyr 8979, or CDC Type-1 protocols; Comes with a free copy of VisiCal software suite that allows it to be configured, calibrated, scanned, monitored or programmed with drag-and-drop and pushbutton simplicity
Control Points: 4 Relays; Control Sequence: Direct or SBO; Relay Contacts: Form C, 0.6 Amps at 125Vac or 2 Amps at 30Vdc; Status Inputs: 8; Status Input Voltage: 12Vdc to 35Vdc; Input Current: .1ma (typical); Isolation: Optical; Overvoltage: phase-to-phase 460V for 10 minutes; Phase-to-Ground 2000V; Input Voltage: 12Vdc (4 watts); Communication Link: 2 RS-232 Ports & 1 Ethernet Port; SWC Certification: ANSI/IEEE C37.90.1 SWC Certified; Dimensions: 7.0" x 7.4" x 1.6"; Also Available as a Bare Card or in a NEMA-4 Box;
Copyright © 2005-2018 Modbus Organization, Inc.
PO Box 628 Hopkinton, MA 01748. All rights reserved.
By using Modbus.org, you accept the terms of our visitor